In this article we are look at the flow of water through an orifice and we will define the orifice as an opening (with closed perimeter) in an element of a flow system. For us this orifice will be a fire sprinkler head or water mist nozzle in a fire protection system, we can use the k-factor formula for almost any rounded orifice.
In 1644 an Italian physicist Torricelli (a pupil of Galileo and also invented the barometer) discovered that the flow though an orifice varied to the root of the pressure and later determined the following basic relationship:
Q = AV
when:
Q = flow from the orifice
A = cross sectional area of the orifice
V = velocity
This has lead to the accepted theorem for flow though a round orifice:
Q = A√(2gh)
The formula above is theoretical and once we take in to account the affects of friction, turbulence and the the contraction of the water stream the formula can be simplified to what we know as the k-factor formula for fire protection system by reducing its complexity to a single constant "k".
The K factor formula for fire protection
When we start any hydraulic calculation for a water based fire protection systems such as a fire sprinklers, water mist systems the k-factor formula is the first which we will need to use and as it is so fundamental all fire protection engineers must have a good understand of how it works. In its most common form the formula allows us to calculate the discharge flow from a of nozzle (fire sprinkler, water mist or a deluge nozzle) if we are given the head pressure and k-factor, we can also calculate the k-factor or the pressure required with this formula.
The discharge from a sprinkler head or water mist nozzle can be calculated from the formula bellow:
q = kp^{0.5}
when:
q = flow
k = nozzle discharge coefficient or k-factor for head ^{}p = pressure
We can rewrite the formula to give us the k-factor as bellow:
k = q / p^{0.5}
or the pressure as bellow:
p = ( q / k )^{2}
The units which we use are important and much not be mixed. you much also be very cautious with the k factor and insure that you get the correct value for a metric or imperial calculation, the units for both are given bellow:
for metric calculations:
p = pressure in Bar
q = flow in litre per minute
k = discharge constant lpm/Bar^{0.5}
and for imperial calculation:
p = pressure in psi
q = flow in gpm
k = discharge constant gpm/psi^{0.5}
We can also use K-factors for many other applications in fire hydraulics such as flow from a fire hydrant, wet riser outlet, hose reel or foam monitor. In fact the list is almost endless and this is why it is important to be familiar with the above formulas.Often K-factors are given as an imperial value in gpm/psi^{½} this value cannot be entered into FHC without first converting to its metric equivalent Lpm/bar^{½}. To convert gpm/psi½ to Lpm/bar^{½} we need to multiply by 14.4 (Approximate)Example: A sprinkler head has a discharge coefficient of 4.2 gpm/psi^{½} what is its metric equivalent valve. 4.2 x 14.4 = 60.48 Lpm/bar^{½}.We only need to use K-factors to one decimal place so 60.48 becomes 60.5 Lpm/bar^{½}.
Typical k factor values for sprinkler and water mist heads
For many standard type of sprinkler the design standards such as EN 12845 & NFPA 13 specify the standard k-factors and minimum pressure which should be used for different Hazard classifications and design densities. For all other types of sprinkler heads the manufactures data sheet should be referred to for the k-factor and minimum head pressure.
Hazard Class | Design Density (mm/min) | K-factor | Minimum Pressure (Bar) | |
1 | Light Hazard | 2.25 | 57 | 0.70 |
2 | Ordinary Hazard | 5.00 | 80 | 0.50 |
As a designer you must check the k-factor value for the nozzle or head manufacturer and insure its application is correct. You should also seek guidance from the design standard which is applicable.
Hcalc calculator
The Hcalc2 Hydraulic Calculator software will allow you to explore the k Factor formula in more detail and will allow you to calculate the flow, pressure or find the k factor for any nozzle or fire sprinkler. You can freely download and use our Hcalc software.